The F113 Series luminaire shall consist of an injection-molded UV stabilized acorn-diffuser, an aluminum cage, an internal optical system and a mechanically fastened slip fitter (capital). The cage shall consist of four struts and a ring jig-welded together. The cage and the diffuser shall be secured to the cast aluminum fitter with stainless steel hardware. The fitter shall be made of cast aluminum and shall house a ballast assembly. The ballast shall feature quick disconnect plugs for easy maintenance. The ballast shall be factory wired, tested and mounted on a keyholed cast aluminum plate together with a 4kV porcelain socket. Lamps are not included and shall be supplied by others. All electrical components shall be UL listed and labeled.
The fixture shall slip fit onto a 3" OD or 4" OD tenon (specify) and shall be secured to the pole with three sets of two s/s hex socket screws spaced 120 degrees apart (exception: fitters "A" and "H" secure with four s/s bolts at 90 degrees apart).
All applicable parts shall receive a standard electrostatically applied thermoset polyester powder coat smooth semi gloss finish with a four part corrosion inhibiting process.